Panel Genset AMF - ATS (Automatic start and stop Genset).
Functions Of A.M.F (Automatic Main Failure) is:
In Automatic Turning (Start) Genset
when the supply of electricity from PLN Fail / Off
while the function of the ATS (Automatic Transfer Switch) is
Automatic Opening the power suply of generator
and closing suply of electricity
and vice versa
open suply of electricity and power suply Closing of
Automatic when the genset is Supay of electricity back
. Some of the information we need from the consumer is:
1. How Power / Generator Capacity (KVA) and how phase (1 or 3 phase)?
2. PLN's installed (KVA) and how phase (1 or 3 phase)?
Sabtu, 01 September 2012
Panel Listrik WLC ( Water Level Control )
The function of the pump panel WLC is:
- To transfer water from the well / reservoir to the water tank
way of working:
filling water from the well / reservoir to the tank (water reservoirs) are automatically
• pump motor life, automatically to fill the tank (where the water Shelter)
when the water in the tanks (water reservoirs) discharged
• pump motor will automatically shut down to stop filling the tank (water reservoirs)
when a water-filled into the tank / water reservoirs full
• pump motor does not work / turn off automatically when the water well / reservoir depleted,
• pump motors will run / turn on automatically when the water well / reservoir filled
By doing so,
Motor Pump not working continuously
So there is no excessive heat / fire pump engine
Panel Listrik Capacitor Bank
PANEL USE BANK PROFITS KAPISITOR:
- REDUCE COSTS PLN Electricity,
- That is in KVAR.Bisa fell between 10% -30%
- Lower motor load amperage
- Make kosphi 0.99
- Removing the power that is in the motor induktive
- Keeps the motor cool and stable.
Brands are Nokian
Panel Automatic / Manual Synchronizing
In general, the function of synchronizing panel is
the process of merging two or more sources of power.
to obtain a larger power source.
Synchroun do the Genset to Genset,
Genset with PLN or synchroun at medium voltage.
when 2 or more generator sets running together for
supplying an electrical system, the generator must
disinchronkan manual or automatic so
has a phase, voltage and frequency and the same
Electrical Panel Box.
Many electrical panel box made people to safety and tidiness of a Power plant. But few people understand the function of the electrical panel box. This is evident from the observations at the time of installation / UPS. Box looks complicated and invisible path.
With careful planning and a high accuracy electrical box is expected to be simple and easy to understand. If there needs to be simple drawings.
If at any time there are additional electrical installations, such as the installation of the UPS with power. Will easily create a path from an existing panel box. UPS with a large capacity is usually more than 6 KVA, requires a way of securing the bypass line by making the use of MCB or MCCB. If there is damage to the UPS or other electrical installations easily addressed / fixed. In this way it is easy to uninstall bypass UPS or others, while the electricity is working.
How to bypass the installation image that is widely used and secure? For that follow the subsequent review.
Before knowing the heart of the matter, to understand the function of this part of the electrical parts.
Electrical parts are:
3. GFCI / RCCB / ELCB
5. cable colors
7. Surge Arrest
Electrical Panel - Electrical switchboard or so we are familiar with electrical panel formed by the arrangement of electrical components that deliberately structured in a board control, so as to facilitate its use.
Tuk more familiar with the function of the electrical panel we telebih formerly known electrical panel components, and must understand the functioning of the electricity itself-this part
Here are a few electrical panel components and their functions you need to know
MCB, which stands for (Miniature Circuit Board) is a component of the electrical panel switch current limiting function as a result of the increase in power / voltage that exceeds the limit and or short circuit. Electrical panel components are usually limited to a small nominal currents up with less than 100 amperes. The shape is there that one pole (one input and one output), there is a two-pole, three-pole and four pole.
MCCB, MCCB Moulded Case Circuit stands Breaker. Circuit Breaker when there is current limiting load current that exceeds the limits. MCCB is used almost equally with the MCB but with load current limit that is greater than 100 amperes to 1600 amperes with.
GFCI / RCCB / ELCB, Ground Foult Circuit Interruption Circuit Breaker is a kind of reply to react faster than the MCB. Electrical panel components will monitor electricity more detail and if there is a wiring short or chipped and the man, does not lead to death.
Grounding, Grounding on the installation and electrical panel components function as electrical safety. Electrical safety consequences of the cables that body part was chipped and the electronic equipment or electrical equipment that later on people. By the component electrical panel is the flow of electric current that wild or that do not work will be grounded
Cable colors. Color wires fixed electrical installations in various countries. Tuk Indonesia, electrical cable color is determined by standard ISO or IEC standatd:
a. red, yellow, black works for phase
b. light blue (ocean blue) serves to neutral
c. yellow-green color serves to ground
CT, CT is a component of the electrical panel steel / metal in the form of a circle (ring) or square ring and middle perforated. The function of this electrical panel components, namely a lowering of current and voltage on the box or pane
Star - delta is the circuit to run the electric motor, which at the time of star using a hub. star (star) and moments later turned into a delta (triangle). The goal is to reduce the current high star andavoid high power consumption when the initial starting of a motor.Delta has a low impedance circuit is draining the first time on the run. Remember the power is in use when starting the beginning ofadl. 3x of the normal starting time. For that series star in use.Substitution series of star to delta in doing a few seconds afterruning normal. Star delta connection found on the current ACthree phase star connection (Y), namely the connection of the ends emergency conductor (coil) of each phase meet at one point in that a neutral, common star connection in use on the motor if it requires less current star because each coil gets highvoltage line to neutral (220v). Delta connection that is, when each end konduktorphasa meet each other at a point (rs, st, tr) is the third conductor to form a triangle.